No trees or large shrubs should be planted over or within 3.0 metres of our apparatus, or the proposed route of our apparatus, unless suitable root restriction methods are taken. If root restriction is to be considered it should extend at least 1.5 metres below finished surface level, in which case the minimum clearance between the wall of our pipeline/apparatus and the root restrictor can be reduced to 0.5 metres. Developers should consult an arboriculturist for advice on the minimum clearances required between root protectors and trees/shrubs.
Should our pipeline have to pass between two trees/large shrubs, a minimum clearance of at least 3.0 metres must be maintained between their respective boles, even where root restrictors are installed.
Developers should include a planting layout with their application.
When installing mains in the vicinity of existing trees we will follow volume 4 of the National Joint Utilities Group (NJUG) guidelines – Guidelines for the Planning, Installation and Maintenance of Utility Apparatus in Proximity to Trees.
Stay up to date with the latest Bristol Water updates
We have joined forces with award-winning chippie Salt & Malt at Chew Valley Lake to provide family treats as part of our support for Gromit … Continue reading Snap a selfie for a fee meal
Maybe it’s nearly lunch time and I‘ve been thinking about where to eat. Bristol is one of the most vibrant cities in the UK with … Continue reading Hungry for a local approach
Only 4% of the 150 litres of water we use each day is for drinking. The water industry is interesting as it is one of … Continue reading Saving Water
Whether you are having a family day out or taking part in one of the outdoor activities around the lake, our restaurants are the perfect … Continue reading Eating and Parking