No trees or large shrubs should be planted over or within 3.0 metres of our apparatus, or the proposed route of our apparatus, unless suitable root restriction methods are taken. If root restriction is to be considered it should extend at least 1.5 metres below finished surface level, in which case the minimum clearance between the wall of our pipeline/apparatus and the root restrictor can be reduced to 0.5 metres. Developers should consult an arboriculturist for advice on the minimum clearances required between root protectors and trees/shrubs.
Should our pipeline have to pass between two trees/large shrubs, a minimum clearance of at least 3.0 metres must be maintained between their respective boles, even where root restrictors are installed.
Developers should include a planting layout with their application.
When installing mains in the vicinity of existing trees we will follow volume 4 of the National Joint Utilities Group (NJUG) guidelines – Guidelines for the Planning, Installation and Maintenance of Utility Apparatus in Proximity to Trees.
Stay up to date with the latest Bristol Water updates
I’ve spent my week living with the same amount of water as people from other countries. On some days, I had as little as 4 … Continue reading Rob’s top 5 tips for saving water – Blog
So, over the past week, I have been living with less water than the average Brit. Why? Mainly because I don’t keep my mouth shut … Continue reading Living with less water – Blog
Only 4% of the 150 litres of water we use each day is for drinking. The water industry is interesting as it is one of … Continue reading Saving Water
Whether you are having a family day out or taking part in one of the outdoor activities around the lake, our restaurants are the perfect … Continue reading Eating and Parking