No trees or large shrubs should be planted over or within 3.0 metres of our apparatus, or the proposed route of our apparatus, unless suitable root restriction methods are taken. If root restriction is to be considered it should extend at least 1.5 metres below finished surface level, in which case the minimum clearance between the wall of our pipeline/apparatus and the root restrictor can be reduced to 0.5 metres. Developers should consult an arboriculturist for advice on the minimum clearances required between root protectors and trees/shrubs.
Should our pipeline have to pass between two trees/large shrubs, a minimum clearance of at least 3.0 metres must be maintained between their respective boles, even where root restrictors are installed.
Developers should include a planting layout with their application.
When installing mains in the vicinity of existing trees we will follow volume 4 of the National Joint Utilities Group (NJUG) guidelines – Guidelines for the Planning, Installation and Maintenance of Utility Apparatus in Proximity to Trees.
Stay up to date with the latest Bristol Water updates
“Bristol Water…Clearly” is our consultation on our long-term ambitions. The document sets out our long-term ambitions for water services, local communities and the environment out … Continue reading Bristol Water publishes a consultation on its long-term ambitions
Ben Newby, Customer Services Director, Bristol Water. Giving people time and space to think is always a difficult ask in an increasingly busy world. But … Continue reading Harbouring creative thinking – The Gilbert & George way
Only 4% of the 150 litres of water we use each day is for drinking. The water industry is interesting as it is one of … Continue reading Saving Water
Whether you are having a family day out or taking part in one of the outdoor activities around the lake, our restaurants are the perfect … Continue reading Eating and Parking