No trees or large shrubs should be planted over or within 3.0 metres of our apparatus, or the proposed route of our apparatus, unless suitable root restriction methods are taken. If root restriction is to be considered it should extend at least 1.5 metres below finished surface level, in which case the minimum clearance between the wall of our pipeline/apparatus and the root restrictor can be reduced to 0.5 metres. Developers should consult an arboriculturist for advice on the minimum clearances required between root protectors and trees/shrubs.
Should our pipeline have to pass between two trees/large shrubs, a minimum clearance of at least 3.0 metres must be maintained between their respective boles, even where root restrictors are installed.
Developers should include a planting layout with their application.
When installing mains in the vicinity of existing trees we will follow volume 4 of the National Joint Utilities Group (NJUG) guidelines – Guidelines for the Planning, Installation and Maintenance of Utility Apparatus in Proximity to Trees.
Stay up to date with the latest Bristol Water updates
Bristol Water has responded to Ofwat’s PR19 Draft Methodology, published on 11 July 2017. You can find the document in PDF format at the bottom … Continue reading Bristol Water responds to PR19 Draft Methodology
Bristol Water’s pop-up Water Bar won the Big Bang Award for Innovation at the Utility Week Stars Awards on Friday 23 June, which is its third … Continue reading Water Bar picks up third award
Only 4% of the 150 litres of water we use each day is for drinking. The water industry is interesting as it is one of … Continue reading Saving Water
Whether you are having a family day out or taking part in one of the outdoor activities around the lake, our restaurants are the perfect … Continue reading Eating and Parking