No trees or large shrubs should be planted over or within 3.0 metres of our apparatus, or the proposed route of our apparatus, unless suitable root restriction methods are taken. If root restriction is to be considered it should extend at least 1.5 metres below finished surface level, in which case the minimum clearance between the wall of our pipeline/apparatus and the root restrictor can be reduced to 0.5 metres. Developers should consult an arboriculturist for advice on the minimum clearances required between root protectors and trees/shrubs.
Should our pipeline have to pass between two trees/large shrubs, a minimum clearance of at least 3.0 metres must be maintained between their respective boles, even where root restrictors are installed.
Developers should include a planting layout with their application.
When installing mains in the vicinity of existing trees we will follow volume 4 of the National Joint Utilities Group (NJUG) guidelines – Guidelines for the Planning, Installation and Maintenance of Utility Apparatus in Proximity to Trees.
Stay up to date with the latest Bristol Water updates
The Northbound carriageway of the A38, Gloucester Road is now open following last weeks burst main. Repairs had been expected to last until Tuesday 28 … Continue reading Burst water main on Northbound A38, Gloucester Road
Nearly 70% of businesses in the Bristol Water supply area are ready for the new retail market, according to a new survey. The new water … Continue reading Businesses are primed for the new water market